## Adiabatic Cooling, Blower Settings, and Why You Care

Just so you don't get bored and quit reading, let's get straight to the point.

When the blower runs for more than a few minutes after the system has cycled off in cool mode, the air may continue to be “cooler” (lower sensible temperature) coming out of the supply, but the heat content of the air will remain unchanged.

The only reason I say “may” be cooler instead of “will” be cooler is that we are assuming there is moisture on the coil or in the pan, and the indoor RH is less than 100%.

Translation: When you run the blower once the system has gone off in cool mode, you will continue to cool for a while, but that extended cooling comes from the evaporation of water out off of the coil and out of the pan. That results in sensible cooling and greater sensible efficiency but also increased indoor humidity.

Translation of the translation: It may feel cooler, but there isn't any less heat in the air by the time you figure for humidity.

Translation of the translation's translation: If you live in a humid place, run shorter off-cycle run times, and think twice before running the fan in the “on” position. If you are in a dry place, then let it blow until your heart is content.

Whenever cooling occurs by direct evaporation of a substance into an airstream (think a swamp cooler), it occurs at no net decrease to the heat content in the air. The heat is just going from sensible (what you can measure with a thermometer) to latent, resulting in higher relative humidity air.

If you go below this line, it is going to get nerdy—BEWARE!

Now, let's talk about why, but first, let's cover some terms.

Heat = Molecular energy or total molecular movement within a substance
Temperature = Molecular velocity, the speed that the molecules are moving
Adiabatic Process = A change in temperature without a change in heat content

Think of an adiabatic process like this: You have a whole room full of ping pong balls bouncing around in a zero-gravity room. The balls are molecules, their total motion is the amount of heat, and their speed is temperature. If you were to change the size of the room by bringing in one of the walls, the balls would bounce faster because the available space was decreased, so the “temperature” would increase. However, the number of balls and the total motion would remain constant (this is what happens to the refrigerant in a compressor, by the way). If you were to move a wall outward and increase the size of the room, the speed of the molecules would decrease, resulting in less speed and lower “temperature.” All the while, the number of balls and the total motion remained constant (which occurs at the outlet of the metering device). In both examples, temperature (sensible heat) changes, but the total heat content does not change; these are both examples of an adiabatic process due to compression and expansion of contained molecules.

Evaporation of water is a process where heat is absorbed into water molecules. They evaporate from liquid water and become entrained in the air as a vapor, displacing some of the nitrogen and oxygen in the air. When that heat is absorbed from the air into the water, it results in lower sensible temperature, but the water is still CONTAINED IN THE AIR. This means that while the air may be cooler, it still has all the heat contained in it in the form of water vapor.

Now for the real shock:

Water vapor is NOT denser than dry air at the same temperature; it is actually less dense/lighter than dry air. However, it does contain more heat (enthalpy—for you nerds like me). That means that when you run the blower after a cooling cycle, the moisture on the coil and in the pan are evaporated back into the space, and depending on the RH of the air, it will lead to sensible cooling but latent gains. That means cooler but higher RH, which is due to the higher heat content of higher RH air at the same temperature.

Once again, depending on where you live, this may be positive or negative.

In Arizona or Colorado? Run that blower after the cooling cycle.

Florida? May wanna shut it off right after the cycle, or maybe 90 seconds at most; leaving the fan in the “on” position will likely result in a small increase of indoor RH.

—Bryan

P.S. – I also did a Facebook Live Video about it today:

Also, here are some great videos on the subject by Jim Bergmann:

## Related Tech Tips

Motor Overheating
An important rating on motors is the AMBIENT  temperature rating that the motor can operate at. This rating refers to the temperature of the air around the motor, not the temperature of the motor itself or even the temperature of the outdoor air—since the motor is often in a condenser air stream that is higher […]
Leaking (Bypassing) Valves
We had a class with our refrigeration techs, and the topic of leaking and bypassing service “angle” valves and ball valves came up. One of the techs pointed out that most valves recommend loosening the top nut on ball valves and the packing nut on angle valves before turning the stem for maximum longevity of […]
Ohm My
One of the most common mistakes I hear techs make is confusing zero ohms with infinite ohms. The fuse above is showing near-zero ohms, which indicates a good electrical path with very little resistance. If there is a perfect path, it would have zero ohms (which isn't actually possible unless you happen to be […]

### One response to “Adiabatic Cooling, Blower Settings, and Why You Care”

1. Jeff B says:

Br’Y’an,
Thanks for all the info you put out here for us. As a newer tech I’m finding to few have an understanding of how or why things are supposed to be…. so again thanks! Also get Bergman on any chance you can…

This site uses Akismet to reduce spam. Learn how your comment data is processed.