## What is Enthalpy?

Enthalpy is easy. It's just a state function that depends only on the prevailing equilibrium state identified by the system's internal energy, pressure, and volume. It is an extensive quantity. Simple.

Like most things, the scientific definition is as clear as mud. In HVAC/R, we use enthalpy measurement to come up with the total heat change in a fluid, whether it's refrigerant, water, or air. You may have even seen a pressure-enthalpy diagram before.

Charts like the one above show how changes in enthalpy correspond to changes in pressure throughout the system. As you can tell, the overall heat content heavily increases and decreases in the evaporator and condenser, respectively. There is also a smaller increase during compression. However, we can measure enthalpy in the air around us, not just in the refrigerant.

In any case, the total change in heat content or enthalpy change is called delta H (ΔH), which is just another way of saying “total heat split.” We generally measure it in BTU/lb in the US.

When we calculate the enthalpy of the air, we need to use probes that measure humidity and temperature, like the HUB2 probes shown above or the Testo 605i probes. Air contains both the energy associated with the temperature of the air (sensible heat) and the latent heat stored in the water vapor. So, HVAC equipment moves both sensible and latent BTUs.

UEI HUB Screenshot

#### Using enthalpy to calculate the total BTUs moved

If you want to use the Δto calculate the total heat added or removed from the air in BTUs, you can use this formula:

Total Heat = (H1-H2) x 4.5 x CFM

In the case above, it would be:

Total Heat = (29.68 – 22.77) x 4.5 x 730 (CFM we measured)

so

29.68 – 22.77 = 6.91 Δ

6.91 x 4.5 x 730 = 22,699.35 BTU/hr

This total air enthalpy change is a required part of calculating total system capacity, and it's a pretty simple thing to understand. If you'd like to see how I measure enthalpy in the real world, check out THIS video.

Don't confuse ΔH (total heat change) with ΔT (temperature difference). ΔH includes both latent and sensible heat and is a measure of heat quantity in BTU/lb, while ΔT only calculates temperature difference and isn't converted to BTUs at all.

—Bryan

P.S. – I also released a short podcast about enthalpy a while ago. If you'd like to listen to a slightly different way of explaining the concept, you can listen to that podcast HERE.

P.P.S. – Enthalpy is also a significant player in the net refrigeration effect (NRE). To learn more about NRE, check out THIS tech tip.

## Related Tech Tips

What Causes Voltage Drop and How to Deal With It
Voltage drop is one of those topics we often mention but seldom think about in-depth. From a very basic standpoint, we need to know whether or not the rated voltage is being delivered to the device or appliance while under full load, which is as simple as running the equipment and measuring the voltage at […]
Why You Need a Torque Wrench (or Two…)
I’ve got a confession to make. I'm “that guy.” Call it OCD, call it being anal-retentive, but I'm always making an effort to be as technically correct as possible. One aspect of that effort has been the use of torque indicating or torque limiting tools when tightening fasteners. It started after I put new valve […]
Setting Sights on Safety: Eye/Face Risks and PPE
DISCLAIMER: HVAC School is NOT an official OSHA safety training resource! Although we provide safety tips in good faith, our website is not a substitute for safety training from an authorized OSHA training source. Although we primarily work with our hands, our eyes are one of our most valuable assets in the industry. After all, […]

This site uses Akismet to reduce spam. Learn how your comment data is processed.