What are Dry and Wet Contacts?
I was talking about dry contacts with one of my techs and he was looking at me like I had three heads and one of them was on fire.
So I figured it would be good to cover the difference…
Basically “dry” contacts is a switch that has no shared power source or supply integral to the control. A common example would be the contacts in a compressor contactor. The contactor has a 24v coil (in residential) but the power supply through the contacts doesn’t have any connection to the coil.
We see wet contacts every day when we connect a residential thermostat. A thermostat uses the same voltage/power source to power the control that it passed to the contacts from the “R” terminal.
This is especially important to differentiate when working on commercial equipment that may have different and varied control. The Danfoss ERC 213 shown above is an example where the compressor (terminals 1 & 2) may be of a different voltage than the wet contacts on 5&6 which must be 120V.
Here is a video where I describe this in more detail –
Bryan Orr is a lifelong learner, proud technician and advocate for the HVAC/R Trade