Uncommon start and run
Quick warning.. guys named Ernie are tough. Don’t mess with dude named Ernie.
He walked up to a box, snatched a pen out of his shirt pocket and scribbled a circle, 3 dots and three numbers on it while grunting “which is common, start and run”
I was in luck….
While I may have had almost zero practical knowledge of air conditioning, this was one thing I HAD actually learned in school.
I marked the terminals and I got the job.
Before you say that this information is useless let me stop you.
It isn’t useless. It may not be something you use every day, but I have needed to ohm out a motor or compressor a handful of times and it got me out of a pinch.
So here it goes –
The lowest ohm reading is between Common and Run
The middle ohm reading is between Common and start
The highest ohm reading is between start and run
Common is just a point between start and run and therefore the common to start and run to start readings will add up to the run to start reading.
Here is how I remember this (let the mockery begin)
Starting is hard… so it has the highest resistance
Running is hard also… but not as hard as starting, so it has a resistance less than start.
Common is easy… being common requires the lowest resistance
So common to run is the least and start to run is the most.
Understanding common, run and start is uncommon… so it requires a lot of resistance… so start… knowing it
OK, I’m done.