Get Tech Tips
Subscribe to free tech tips.
TXV Bulb Placement
When mounting a TXV bulb or checking bulb placement, there are a few important considerations (listed in order of importance):
- Mount the bulb on the suction line. Flapping in the breeze is no good.
- Mount it TIGHTLY with a proper metallic strap (usually copper, brass, or stainless steel)—not with zip ties or tape.
- Position it on a flat, clean, smooth portion of the horizontal suction line—not on a coupling or an elbow.
- Mount it before the equalizer tube (in other words, put it closer to the evaporator than the EQ tube).
- When possible, mount it at 8 or 4 o'clock on the suction line (or according to manufacturers' specs). This becomes more important the larger the suction line.
- When possible, insulate the bulb so that it is not influenced by the ambient air temperature. It never hurts to insulate the bulb, even inside the cabinet, though not all manufacturers require it.
- If you do need to mount it vertically, make sure the tube points up, not down.
Poor bulb contact will (generally) result in a bulb that is warmer than desired, resulting in overfeeding and lower than desired superheat.
Finally, be gentle with the bulb and tube. They break easily.
You can read a more detailed description HERE.
2 responses to “TXV Bulb Placement”
Leave a Reply
Related Tech Tips
High Capacity Amperage Measurement
We had a situation a few months back where we needed to monitor amperage on a grocery store panel over a period of time. The trouble was that we needed data-logging capability AND accurate measurement at 600+ amps. Finding an all-in-one solution proved to be quite expensive. Luckily, my friend Jim Bergmann happens to own […]Read more
Why Measuring Static First Isn't Always Productive
There is a big move in residential and light commercial HVAC toward measuring static pressure regularly during commissioning, service, and maintenance. Don't get me wrong… Measuring static pressure is VERY important. The challenge comes in when techs begin taking measurements without understanding where to take them, what they mean, or worse: they use measurements as […]Read more
Salamander Broiler Cleaning
This article was written by up-and-coming young tech and new contributor Kaleb Saleeby. Thanks, Kaleb! Recently, I came across a work order description in my dispatch that made me scratch my head. Clean Salamander broiler I had to ask the omniscient Google for answers. It turns out it has nothing to do with vividly-colored, “fireproof” […]Read more
Good tips, but it might be worth mentioning that some manufacturers recommend in their literature to relocate the bulb outside the plenum/cabinet.