Why and How to Adjust a TXV/TEV
As we discussed in an earlier podcast, a TXV maintains a specified and constant superheat at the evaporator coil outlet. It does this through a balance of forces between the bulb pressure (opening force), equalizer pressure (closing force), and spring pressure (closing force). We can actually adjust the spring pressure on some valves. But why […]Read more
What’s So Wrong With “Beer Can Cold”?
First off, if you've never heard the term “beer can cold,” you are either not in the trade, or you have been living a pretty sheltered existence. I started as a tech apprentice when I was 17 years old, and on my first day in the truck, my trainer grabbed the suction line of a […]Read more
Negative Superheat? Time to Check Your Tools
I was fresh out of school, working as an apprentice at my first real HVAC job, and I was listening in on a shop conversation between a few techs. They were talking about finding so many overcharged systems. One of the techs turns to me and says, “I had a unit yesterday that was so […]Read more
What Should My Superheat Be?
The most common—and often most frustrating—questions that trainers and senior techs get asked sound something like this: “What should my ______ be?” or “My _____ is at ______. Does that sound right?” Usually, when the conversation is over, both the senior and junior techs walk away feeling frustrated because the junior tech just wanted […]Read more
The “5 Pillars” of Residential A/C Refrigerant Circuit Diagnosis
Suction pressure, head pressure, subcooling, superheat, delta T. Taking all five of these calculations into account on every service call is critical. Even if you must do further diagnostic tests to pinpoint the problem, these five factors are the groundwork before more effective diagnostics can be done. I would also add static pressure as an […]Read more
The Case for Checking the Charge Without Using Gauges
Jim Bergmann and I recorded a podcast for HVAC School that covered when and how to check the refrigerant circuit without connecting gauges. Listener Joe Reinhard listened several times and wrote up this summary of what he gained from the episode. I edited it lightly, but most of this is his work. Thank you so […]Read more