Size and Orientation of Return Grilles and Supply Registers
Proper sizing and orientation of grilles, registers, and diffusers may seem like such a simple thing, but it’s an area where confusion and mistakes are commonly made.
First let’s define some terms.
A return draws air into a return duct system with negative pressure compared to the space usually via a fixed “grille” but also often called a “return vent” or a “return intake vent” or for some of you old school folks from up north the “cold air return”.
The supply vents, registers or diffusers blow air into the conditioned area with positive pressure and are responsible for distributing and mixing the air.
A vent is a generic word for a designed opening or cover that air passes in or out of. When in doubt, just say vent.
A grille is a fixed vent type that contains no damper or adjustable louvers. Grilles can be used for supply but are most commonly used in return applications. The grille shown above is a steel stamped return grille.
A register is a vent that contains an internal adjustment damper and often externally adjustable louvers. Registers have the same inlet neck and outlet face size. Air will move straight through registers and grilles. Registers are the most common type of supply vent. The register shown above is a common aluminum, adjustable, curved blade, one-way 10×6 ceiling register.
A diffuser is a vent that has a smaller inlet and a larger face resulting in a lower face velocity than that of the inlet duct. Diffusers often “turn” the air at a steep angle as it exits the face. Diffusers may or may not have adjustable dampers or louvers. The diffuser shown above is a typical tiered, acoustical ceiling 2’x2′ lay-in supply diffuser.
Sidewall Straight Blade vs. Curved Blade Ceiling
Sidewall registers and grilles have straight louvers to force the air straight into the space with no turning at all at the face. Curved blades direct the flow at an angle and are generally used for ceiling applications.
When sizing grille or a register you will measure the OPENING that the grille or register is designed to cover or recess into, not the total external frame size of the grille or register. The register shown below is a 10×6, sidewall supply register.
Look at the image at the top of the article. This is generally how we describe return grille orientation because return grilles are an instance where grille orientation / louver direction make a big difference.
For return grilles, we state the dimension parallel (running the same direction as) with the louvers first and then the perpendicular dimension second.
For supply diffusers, they are almost oriented with the external louvers parallel with the long dimension on ceiling registers and with the louvers parallel with the short dimension on wall and floor registers like the shown below.
For floor registers, they follow the same rules as return grilles where you state the dimension parallel to the louvers first. This means that floor registers will often be smaller number first like 4×10 or 4×12.
Ceiling and some sidewall registers will usually just be described as long side first such as a 10×6 or 12×8 but that can vary from brand to brand.
Yes, it is pretty simple, but also essential for clear communication.
P.S. – This episode of the podcast with Jack Rise covers common duct and vent mistakes that you may want to know.