RH, DB and WB
I recently received a message asking for a discussion of RH. WB and DB again. Time and time again I hear techs say that condensation occurs when “hot meets cold” which may be true in some cases but that is only a small part of the story.
RH = Relative Humidity as in the percentage of humidity relative to the amount of moisture can hold at that temperature.
I like to think of it like sugar in a cup of coffee. The hotter the coffee the more sugar the coffee can hold.
It’s a common misconception that hot air tends to be more humid. While it’s true that hotter air can hold more moisture in the same way that hotter coffee can hold more sugar it does not mean hotter means more humid. In fact, if you heat a mass of air and the amount of moisture doesn’t change the RH will go down as the air gets warmer. This is why the RH coming out of the top of a furnace is lower than the RH going in. No change has occurred in the actual amount of moisture present, the air is just hotter and therefore lower in humidity relative to how much it can hold.
DB = Dry Bulb and is the temperature of air without taking account for evaporation / relative humidity
WB = Wet Bulb and is the temperature of the air with the evaporative effect of a “wet bulb” taken into account. Quite literally wet bulb temperature is the temperature a thermometer bulb will be when covered in a wet fabric and whirled in the air or placed in an airstream.
If the RH is below 100% the WB will always be lower that the DB. The differential between the DB and WB illustrates the RH. The higher the differential the lower the RH. The lower the differential the higher the RH. When DB and WB read the same then the RH is 100% and the air is “saturated” and no more evaporation can occur.