Get Tech Tips
Subscribe to free tech tips.
Refrigerant Recovery Practices
Recovery is the removal of refrigerant from a system. From there, you can either store it and send it in for recycling or to reintroduce it back into the same system.
Here are some top tips:
- Make sure your tank is empty and evacuated to 300 microns if you plan to return the refrigerant back into the system.
- Never mix refrigerants.
- Purge your hoses before recovery.
- Use a flare line drier on the inlet of the machine to increase the life of the machine and to filter and dry the refrigerant. These must be replaced regularly.
- When recovering into a tank using the standard method, invert the tank and pump into the vapor port on the tank.
- Remove Schrader cores before recovery for faster recovery and a cooler tank.
- Use larger gauge hoses with no core depressors for faster recovery.
- Check the recovery machine inlet screens regularly. Clean or replace them as needed.
- Some machines require oil to be run through the machine from time to time. Read manufacturer specifications.
- If your tank becomes hot, you can either place it in a bucket of water or run water over the tank.
- Do not leave refrigerant in your machine during storage. If your machine has a purge mode, make sure to purge the refrigerant out of the condenser (see manufacturers specs on your machine).
- Most HVAC systems holding under 200 lbs of refrigerant are not required to be pulled into a vacuum during recovery. See this chart from the EPA.
- Weigh the refrigerant out and do not fill the tank to more than 80% of the REFRIGERANT capacity, not just the water capacity.
We cover all of this and more in this video:
Related Tech Tips
A Tale of Two Latents
When the quiz or the teacher asks what “latent” heat is, there is generally some reference to it being hidden heat, which is what the word “latent” means. We then learn that it is heat energy transferred that results in a change of state rather than a temperature change. Later on, we hear a lot […]Read more
Something You May Want to Consider on Every Call
There are a few important things that I suggest checking on every service call to reduce callbacks and increase customer satisfaction. One of them that often gets missed is preventing wire rub-outs. One of my area managers and experienced tech Jesse Claerbout shot a video showing the simple step he takes to prevent major damage. […]Read more
To maintain combustion (burning), you need three things: fuel, heat, and oxygen. If you have all three in the proper proportion, you can maintain a continuous state of combustion. Remove one (or reduce one sufficiently), and the triangle of combustion can collapse. In a common natural gas (NG) furnace, the heat is the igniter, the […]Read more