Get Tech Tips
Subscribe to free tech tips.
Nick Basic Electrical Circuits June 20, 2021, 5:13 pm
Related Tech Tips
Relative Humidity in the Supply Air Stream
When you first start checking your supply air with a thermo-hygrometer, you may notice that the relative humidity is REALLY HIGH. Often, the RH in a supply duct will be between 85% and 96% relative humidity on a system that is functioning as designed. The reason for this is fairly simple: In order for dehumidification […]Read more
Start Flowing Nitrogen Sooner
My technician (and brother-in-law), Bert, made a good point. (It's hard for me to admit it, but it's true.) When he needs to open the refrigerant circuit to make a repair, regardless of whether he is recovering or pumping down, he pulls out his nitrogen tank and his regulator. (We like the Western Enterprises VN-500 […]Read more
Why (and When) Do We Need Defrost?
Why Defrost? Let's start with the basics and move on from there. Defrost is necessary when the coil temperature drops below 32°F. Defrost can be as simple as turning the compressor off for a period of time or as elaborate as reversing the flow of refrigerant for the whole system or just parts of the […]Read more