Get Tech Tips
Subscribe to free tech tips.
HVAC/R Evacuation Quiz January 2, 2022, 3:35 am
Related Tech Tips
How much PRESSURE is that Recovery Tank Designed For?
Most techs know that you shouldn't fill a recovery tank more than 80% with liquid-based refrigerant. Many know that the WC rating stands for “water capacity.” So, you need to adjust for the density of the actual refrigerant rather than just using 80% of WC. I hope most of you know that the TW marking […]Read more
The "Approach" Method of Charging and Condenser Efficiency
We have discussed many methods for checking a refrigerant charge without connecting gauges over the last few years. Recently, I've been thinking about the “approach” method of charging that many Lennox systems require. What is the Approach Method? The “approach” simply refers to the temperature difference between the liquid line leaving the condenser and the […]Read more
Air Changes Confusion
Air changes per hour (ACH/ACPH) simply describes how many times the quantity of air in a room (or structure) is completely replaced per hour. If you have a 10'x10'x10′ room, the room contains 1000 cubic feet of air. If the supply and return to the room is supplying a balanced 100 CFM (cubic feet per […]Read more