Jesse Grandbois is a tech who reads the tech tips, and he wrote a few tips that he wanted to share on some gas furnace control basics. This tip is about how to use a fancy digital stat on a millivolt system.
For those of you who don't know, a millivolt system uses a thermocouple/thermopile with a standing (constant) pilot flame to generate a tiny “millivolt” signal used to control the furnace rather than the 24v signal modern thermostats use.
There's still a ton of millivolt furnaces out there, and many of the owners want the new and fancy wi-fi thermostats. If you're not sure how to get the 24v out of a millivolt system, this tip is for you.
But first, let's go over a couple of basics.
You'll be using an isolation relay. It's just an SPST (single-pole, single-throw) NO (normally open) relay to separate the different voltages in a system.
Millivolt furnaces operate using a thermopile to power the system. A thermopile is simply multiple thermocouples. Some millivolt systems will also use a thermocouple for flame safety. Under load, a thermopile should operate at no less than 190MV.
Please refer to the wiring diagram while reading the information below.
You're going to feed 120v to the transformer. This is what will be used to create the 24v for the thermostat.
Wire your hot side of the 24v transformer to R on the Wi-Fi thermostat.
Connect W on the thermostat to one side of the relay coil. On the other side of the coil, you'll add C from the thermostat and common wire of the transformer.
You're going to take the thermostat wires off your old millivolt thermostat and add them to the NO terminals on the relay.
On a call for heat, the relay coil will be powered, closing the SPST relay powering the millivolt system (NO terminals) for heat.
Microchannel is a coil type used in many evaporator and condenser coils. You can easily identify it by its flat tubes, and its fins look like waves between the tubes. The technology was developed for use in the automotive industry and is used for radiators and automotive A/C condenser coils. These coils are made of […]
We may not realize it, but heat transfer inside our homes keeps the HVAC industry afloat. Without air conditioning in the summer, our buildings would remain stuffy, miserable places. That’s because heat can come from the outdoors, indoor objects (such as cooking appliances), and our bodies. So, this article will cover the three main types […]
For years, I've worked with and around people who view work, problems, and goals differently than I do. I've often told my wife that I have an issue managing and leading administrators, salespeople, and other inside staff. Why? It's because I just don't communicate in a way they seem to like. It's been 20 years […]