## What is the “Mid Point” of a Refrigerant Blend?

As we have mentioned in several previous articles (such as this one HERE), many blended refrigerants have glide, which simply means they boil and condense over a range of temperatures instead of just one temperature.

As an example, consider refrigerant R407c. It is a zeotropic blend, which means it has enough glide to make a big difference if you fail to consider it.

For example, on an evaporator coil running R407c, the refrigerant leaving the TXV will begin boiling at the bubble point. Let's say that the pressure in the evaporator is 80 PSIG; the bubble temperature will be 40°.

As the refrigerant continues boiling, the temperature will increase towards the dew point, which is 50.8°. Any temperature gained ABOVE 50.8° on an R407c system at 80 PSIG is superheated, meaning the refrigerant is 100% vapor.

So, we calculate superheat as the temperature above the dew point and subcool as the temperature below the bubble point. The condensing temperatures and evaporator temperature aren't fixed, but they GLIDE between the bubble and dew and back again when the refrigerant is changing state.

But what does this mean for the evaporator and condensing temperatures when calculating target head pressure (condensing pressure) and suction pressure (evaporator pressure), also known as evaporator TD and condensing temperature over ambient?

The simplest way is to use the midpoint between the dew and bubble points to calculate CTOA and DTD.

In the case above, you would simply calculate 50.8° + 40° = 90.8 | 90.8 ÷ 2 45.5° average evaporator temperature or midpoint

Emerson points out that evaporators would be better calculated using 40% of bubble and 60% of dew, but the extra complexity generally doesn't make enough difference to mention.

I made this video to demonstrate further:

—Bryan

## Related Tech Tips

Impacts of Decreasing Evaporator Airflow
Airflow, airflow, airflow… When we set up and commission comfort cooling and heating systems, we need to pay more attention to airflow before worrying about the fancy controls or the refrigerant circuit. So, as a thought exercise, let's consider a typical 2-ton, straight cool, TXV residential system and think through what happens when we alter […]
What is Isentropic Compression?
This article deals heavily with entropy. Entropy is not a simple topic, so we highly recommend checking out HVAC School’s Entropy in Refrigeration and Air Conditioning for some background information. Describing isentropic compression is a daunting endeavor. We all recognize the term compression, and I’m sure most of us can deduce that isentropic has something […]
Is It OK To Top Off With R410a?
I am consistently surprised by how much false information still circulates out in the field, and one of the ones I hear often is the idea that you cannot or should not “top-off” or recharge R410a systems on top of an existing charge of R410a when the system is low. So, to be clear, before […]

### 4 responses to “What is the “Mid Point” of a Refrigerant Blend?”

1. Patrick Dwyer says:

Thanks.

2. Dave says:

¡Gracias caballero! Had to put on my youtube watch later list…as well to refresh at another time.

Like the sidebar action showing the closeup on phone app!!

3. Matt says:

I’ve used SuperDew and SubBubble to help me remember

4. Carroll Price says:

Well presented. Thanks.

This site uses Akismet to reduce spam. Learn how your comment data is processed.