## Connecting Transformers in Parallel

I had an old-timer tell me that you can never connect two transformers together because they will “fight one another.”

If you are anything like me (and heaven help you if you are), a cartoon in your head starts playing whenever someone says something like that.

In this case, I imagine two transformers with boxing gloves on duking it out to see which one “wins.”

The truth is that you can connect two transformers so long as you are careful, but you need to know why you're doing it. Then, of course, you need to do it properly.

Transformers have a VA (volt-amps) rating that dictates how many volt-amps the transformer can handle on the secondary. (Volt-amps, mathematically represented as volts x amps, are watts simplistically, but there is a more complicated reason they are called VA in transformers. However, we won't get into that here.)

Above, we show two 75VA transformers with 24V secondary windings.

75VA ÷ 24V = 3.125A

So, with a 75VA transformer, you can run a maximum of 3.125 amps. If you need more power, you would need to either get a larger, more expensive transformer or connect another identical one in parallel. If you connected two 75VA transformers in parallel, you would then have 150VA of secondary capacity, which can be necessary in some cases with multistage commercial units or some large accessories.

In this case, parallel simply means connecting the two primary and secondary windings exactly as we show above.

Pretty easy.

It is SUPER important to get the polarity exactly the same and use two transformers with identical winding turns in the primary and secondary and identical secondary coil impedance (resistance).

In fact, it is so important that I advise that you only do this if you have two identical-model transformers.

To be even safer, connect the primary windings first and check the secondary's against one another with a voltmeter before actually connecting them to the system. For a typical 24v secondary, you can connect the two common wires to ground to act as a stable reference first, and then you can check the two R or hot side leads to one another and then to common. They should read 0v to one another and 24v to common. If you get anything other than 0v from hot to hot, you want to recheck your primary wiring and ensure they are exactly the same.

—Bryan

## Related Tech Tips

We’ve already made a few tech tips and uploaded a few podcasts about HVAC business practices, including some on profitability. That content is all fine and dandy, but those podcasts, articles, and videos may seem out of touch with most of our audience. After all, that content hardly seems to apply to the bread […]
Determining the Air-Side Charge of an Expansion Tank
Michael Housh from Housh Home Energy in Ohio wrote this tip to help techs determine the air-side charge on a pressure tank. Thanks, Michael! Determining the air-side charge of an expansion tank in a hydronic heating system is a relatively easy task.  A properly sized and charged tank is designed to keep the system pressure […]
Simple Pump Selection Part 2
Another follow-up article by Michael Housh… Enjoy! In this article, I thought I would show a pump curve and match it up with our system head-loss curve that we created in the last article, but before I do that, I thought I would talk a little bit more about the system head-loss curve and why […]

### One response to “Connecting Transformers in Parallel”

1. Genry Garcia says: