Get Tech Tips
Subscribe to free tech tips.
Changing Liquid Filter/Drier Cores Tip
This tip comes from market refrigeration and controls technician Kevin Compass. Thanks, Kevin!
A little tip when changing liquid cores:
If you start pumping them down, begin bypassing discharge gas into the shell to warm it up, push out the remaining liquid, and bring the shell above the dew point so that it doesn't sweat when you change the cores.
This helps drive out the liquid refrigerant in the shell and helps prevent moisture contamination from condensation in the shell.
Work quickly so that the system is open for the shortest possible time.
Two spring clamps make holding the lid on the cores cake so that you can put the bolts back the easy way.
Related Tech Tips
Does the Voltage or the Amperage Kill You?
I hear the following phrase a lot: It's the amperage that kills you, not the voltage. While there is truth to the statement, it is sort of like saying, “It's the size of the vehicle, not the speed that kills you when it hits you.” OK, so that's a pretty bad example, but hopefully, it […]Read more
The Two OTHER EPA violations
We all know (or should know) that venting refrigerant is a big no-no and can result in trouble from the EPA. There are many other potential violations, but two of them can easily occur if you aren't thinking ahead at the disposal of mercury and oil. Mercury is found in fairly large quantities in the […]Read more
Ideal Gas Rulebreakers
Breaking the Sound Barrier So, what do you think of when you hear an “ideal gas?” R22, R12 maybe… natural? Take a look at the F-18 above. It's breaking the sound barrier, and that cloud is a shockwave. It has nothing to do with this article, but I think it's pretty darn cool! An ideal […]Read more