Get Tech Tips
Subscribe to free tech tips.
Cased Coil Misalignment
On occasion, you will either find a furnace or be tasked with installing a furnace where the coil overlaps the edge of the furnace because the coil is wider. In the case of a Carrier CNPVP coil, you need to ensure that you align the coil according to the manufacturer's specs, or you risk cutting off about 1/3 of the airflow.
The best-case scenario is to use a coil that is a sizer match for the coil, or you can buy or make a tapered metal transition between the furnace and the coil. In the case of the CNPVP, the manufacturer allows the coil to be offset to the left.
In this video, we illustrate replacing a leaking coil and reconfiguring it in the proper orientation.
Related Tech Tips
Don't Forget the Suction Filter Drier
Courtesy of Emerson It is important to have refrigerant free from debris and contaminants, and we control these issues on many different fronts. 1. Proper tubing handling prevents copper shavings, dirt, and water from entering while installing. 2. Flowing nitrogen while brazing prevents carbon build-up. 3. Deep vacuum of 500 microns or less removes air, […]Read more
This tech tip was written by experienced tech and VRV specialist Ryan Findley. Thanks, Ryan. This is a quick overview, not a substitute for taking proper manufacturer training. This tech tip is geared towards the mechanic who is fairly new to VRV systems. As with anything, before we harness the ability to install or […]Read more
Powered Attic Ventilation
When I first started in the trade, I used to advise customers with hot attics to install powered attic ventilators (PAVs) to “suck” that hot air out of the attic. It just made sense to me at the time; if the attic is hot, get the hot out! When I started learning more about design, […]Read more