C stands for “Common Mistake”

You have seen the C terminal on a dual run capacitor before. You have also seen the C terminal on a compressor.

It stands to reason that they would both connect together, right?

They don't connect, and they aren't even related, at least not in the way you think.

In both cases, the C denotes a “common point” in the dual capacitor. It is the common point between the fan capacitor (fan) and the compressor capacitor (herm).

In the compressor, it is the common point between the run and start windings (this is why R+C + S+C = R+S if you ohm a compressor).

The C terminal of a dual capacitor is actually fed from the OPPOSITE leg of power as the C terminal on the compressor. That is because you must power the start and run windings with the same leg and common with the other leg.

A way to remember it is by memorizing:

“The same leg that feeds start feeds run”

The C terminal on a capacitor is actually the common feed for the start winding of the compressor and fan (OPPOSITE side from the fan and herm plates on the capacitor).

So, here are the compressor terminals:

• C goes to one leg of power.
• R goes to the other.
• S goes to the HERM terminal on a capacitor, with the other side of that capacitor (C) going to the same leg that feeds R.

C what I'm saying? Confusing.

With 208v or 240v circuits, the L1 and L2 high voltage incoming lines make no difference as to which one is which when you connect. You could swap them on the L1 and L2 on the contactor, and it wouldn't change anything. But once we decide which is connected to Run and which is connected to common on the COMPRESSOR, we need to hook the run side to capacitor C, not the compressor common side.

There is also ANOTHER common “common” we see, and that is the secondary side of a low voltage transformer that is opposite from R or hot. You may notice that many low voltage transformers have an ungrounded secondary, meaning that either of the wires in the secondary could be hot or common, depending on how you hook it up.

In other words, one side of the transformer is designated HOT because we connect it to the line side of our control switches (thermostats, defrost boards, safety circuits), and common is the common point where all the loads connect on the opposite side of the circuit from the line.

If you are new to the trade and see the designation C or the word common, don't assume it is the same as other C and common terminals and start connecting stuff together… Unless you like creating smoke.

—Bryan

Related Tech Tips

Top 10 HVAC Tech Tips
This article is based on HVAC School’s special video for 100k subscribers. The episode features Eric Mele, Andrew Greaves, and Sam Behncke as special guests. To celebrate HVAC School’s 100,000 YouTube subscribers milestone, we've released a video on a topic that applies to all sorts of HVAC techs. Customers don’t like making callbacks, and we […]
Careful With That 40VA Transformer
A 40VA transformer is rated for 40 VA or volt-amps on the secondary. For a typical 24 volt secondary, this is simply using Watt's law to calculate amperage. (For more information on Watt's or Ohm's laws, please check out this article HERE.) 40 ÷ 24 = 1.666666 ∞ (round up to 1.67 already) So, you […]
Indirect Soldering Technique
As HVAC/R techs, we don't generally do a lot of soldering—unless you are in a shop that has embraced Stay Brite® 8 from Harris. Several aluminum repair products on the market also use an indirect soldering type technique, so this is a general and generic overview of some best practices. As always, follow the manufacturer's […]

4 responses to “C stands for “Common Mistake””

1. Great article! Caps can confuse me sometimes; much clearer understanding now

2. Mike Dubose says:

OR L1 FROM BOTTOM ON CONTACTOR GOES TO TO COMMON OF COMPRESSOR AND FAN
L2 FROM CONTACTOR GOES TO BOTH RUNS ( COMPRESSOR AND FAN)
L2 FROM CONTACTOR GOES TO COMMON ON DUAL CAPACITOR
HERM ON CAPACITOR GOES TO START OF COMPRESSOR
FAN ON CAPACITOR GOES TO START ON FAN
I hope this is a easier way just follow schematic commonly ( red and black wires)

3. Jason Cook says:

I always like the challenge of putting the smoke back in!

4. Seth Yank says:

Does it matter if you connect the common on the cap to the shunt side or the contactor side of the contactor

This site uses Akismet to reduce spam. Learn how your comment data is processed.