32° Saturation (Evap Temperature)
Evaporator temperatures below 32° are common and acceptable in refrigeration, that’s why there is a defrost sequence.
In a heat pump running in heat mode it’s the same, freezing is a part of the process and defrost is necessary.
In comfort cooling… we can’t allow the evaporator to get below 32°… or it will freeze.
I can’t tell you how many times I look back and technician notes and can see in plain black and white that the system will freeze.
And that is not OK…
Freezing causes flood back, no cooling, water damage and biological growth.
We cannot leave a system that is just going to freeze.
The image above is of the Danfoss refrigerant slider app and it shows that when suction pressure drops below 102 PSIG on an R410a system…. the coil hits 32° and will start to freeze.
This means that we need to setup equipment so that it will not freeze during normal operating conditions.
A typical residential A/C system should be setup so that the return temp can get all the way down to 68° and still be just above freezing.
Let’s say it’s 78° in a house on an R410a system and your suction pressure is 108 PSIG (like shown)
Your suction saturation (coil temperature) is 35° and so the coil won’t freeze.
The coil temperature will drop approximately 1° for every degree the return temperature drops. So if the customer sets it down to 74° the saturation will now be 31° and the coil will freeze.
Pretty basic stuff but very important if you don’t want to leave a problem for your customers.
There are many things that can cause this (low airflow, restrictions, low refrigerant) but step #1 is having the wherewithal to catch it.