## Grounding and Bonding Myths

Grounding is an area of many myths and legends in both the electrical and HVAC fields. This is a short article and we will briefly cover only a few common myths. For a more detailed explanations I advise subscribing to Mike Holt’s YouTube Channel HERE

Myth – Current Goes to Ground

Actually current (electrons) move according to a difference in charges / potential (Voltage). When a potential difference exists and a sufficient path exists there will be current. In a designed electrical system current is always returning to the source, the opposite side of a generator, transformer, battery, Inverter, alternator etc… current only goes to ground when an undesigned condition is present and ground (earth) is generally a VERY POOR conductor.

Myth – To Be Safe, Add More Ground Rods

Ground is generally an exceptionally poor conductor. The purpose of ground rods is to carry large spikes in current that comes down your electrical distribution lines away from the building. Adding more ground rods can actually EXPOSE the building to current from near ground strikes.

Myth – Connecting Neutral and Ground Together In Multiple Places Is a Good Idea

Neutral and equipment ground should be connected in only one location at the main distribution panel to prevent ground from carrying neutral current. If equipment ground is carrying any current there is a problem.

Myth – Electricity (only) Takes The Path of Least Resistance

If you have ever wired a parallel circuit you know that electrons travel down ALL available paths between to points of differing electrical charge.

Myth – Common, Ground and Neutral are the Same

Not even close. Common and neutral are terms used to describe the one side of a transformer. They are not grounded unless you ground them and when you do you are designating which side of the transformer will have an electrical potential that is equal with EQUIPMENT GROUND. The earth itself simply acts a really poor and erratic conductor between points of electrical potential that we designate and should not be confused with equipment ground.

Myth – Ground Rods Keep Us From Getting Shocked

Nope. Proper bonding connection between appliances, switches and outlets and equipment ground connected back to neutral at the main distribution panel in conjunction with properly sized circuit breakers and GFCI equipment keeps us safe. Grounds rods have little to nothing to do with protecting you from a ground fault.

Here is a great video on the topic and  you can find an article defining grounding and bonding terms HERE

— Bryan

Scroll to top
Translate »

### Daily Tech Tip

Subscribe to our daily tech tip to receive daily tips and advice!